CINE WORLD Complex, Hemel Hempstead
GES installed, tested and purged over 80 meters of 150mm carbon steel gas line with branches of 80mm, to supply newly refurbished restaurants. AECV and Rotary Secondary meters were also installed in each Unit. Also 120 meters of 76.1mm cold pressed copper pipe work was installed to supply mains water to these restaurants.
GES also carried out a strength test, tightness test and gas purging for gas pipe work and hydrostatic pressure testing, pre-commission cleaning and chlorination of water pipe work.
Gas pipe work was painted ochre yellow, water pipe work was lagged after testing.
Please click on an image to enlarge it.